Category

- Products
- FAQ
- Contact us

Frequency inverter manufacturers

# Matching frequency converter with motor

I have a spare pump in my warehouse that requires 15 horsepower (HP) at best efficiency point (BEP) flow when running at 1,760 rpm. I also have a new application with a duty point that can be matched perfectly by this pump at about 1,466 rpm. This speed is about 83 percent of full speed and equates to 50 hertz (Hz) when operated by a frequency converter. The affinity laws indicate that the power required at 50 Hz is reduced to just 8.7 HP. I have a limited budget and would like to keep my total cost for the motor and frequency converter as low as possible. Is it OK to use a 10-HP motor as long as I make sure the frequency converter will never exceed 50 Hz?

Why was a 10-HP motor not OK? Many ways are available to ensure that a frequency converter will not exceed a maximum preset speed. The reader's plan was flawed from the beginning, and the problem was not with limiting the maximum speed. Centrifugal pumps follow the affinity laws. When the speed of an electric motor changes due to a change in frequency, other rules dictate the motor's performance.

The HP produced by an induction motor is directly proportional to its torque and rotational speed (HP = (torque x rpm) / 5,250). If the number of stator poles remains constant, the rotational speed of that motor is directly proportional to the frequency of the input power. When the frequency changes so does the speed, but the torque remains constant. For torque to remain constant, HP must change. Therefore, if the incoming power frequency is reduced from 60 Hz to 50 Hz (5/6), the HP will be reduced to 5/6 of its original value. If this is applied to the 10-HP motor in the example above, its output at 50 Hz would be just 8.3 HP. Even though the power required by the pump was reduced to about 57 percent (8.7 HP) of its original 60 Hz value, it is still more than the 10-HP motor can supply at 50 Hz.

U.S.-made motors for 60-Hz operation must be de-rated for use overseas on 50-Hz power. The standard de-rating factor for 230-, 460- and 575-volt models is 5/6 (0.83) of the 60-Hz power. Most manufacturers use 0.85 for open drip proof (ODP) motors and 0.80 for totally enclosed fan-cooled (TEFC) motors, assuming a service factor of 1 and line voltages of 190, 380 and 475 volts. If line voltages are higher, the de-rating factor is reduced proportionally.

Application of the proper line voltage at reduced frequencies is important. A motor designed for 460-volt, 60-Hz operation has a volts/hertz (V/Hz) ratio of 7.66. If the same voltage is used at 50 Hz, the ratio increases to 9.2. To accommodate this increase, the motor magnet's circuit size must increase. Because this is impossible, the existing circuit will saturate, causing an increase in current draw and a corresponding increase in winding temperature. Winding temperature plays a major role in insulation life. For 50-Hz operation, line voltage is reduced to 380 volts and keeps the V/Hz ratio at 7.66.

A constant V/Hz ratio is always maintained when a motor is under frequency converter control. When frequency is changed, the line voltage is automatically compensated via pulse width modulation (PWM). If voltage is 460 volts at 60 Hz, it is reduced to 230 volts at 30 Hz.

Figure 1. Relationship for a 15-horsepower motor and a pump with a full-speed power requirement of 15 horsepower

One reason frequency converter is popular in the centrifugal pump industry is the third affinity law: power varies as the cube of a change in speed. If speed is reduced to 75 percent of full speed, power is reduced to 42 percent of full-speed power. If a pump motor is properly sized for full-speed operation, it will always have adequate power at reduced speeds. Motor power reduction is directly proportional to speed reduction while the pump power requirement drops as the cube of a speed reduction. Figure 1 shows this relationship for a 15-HP motor and a pump with a full-speed power requirement of 15 HP.

Figure 2. Relationship for a 10-horsepower motor and the same pump shown in Figure 1

The ratio of available motor HP to required pump HP increases exponentially as speed is reduced. Figure 2 shows this relationship for the same pump and a 10-HP motor. Here, the available HP does not meet the required HP until the speed is below 50 Hz. If the reader's design point could have been met at 45 Hz, the 10-HP motor would have been adequate.

Why was a 10-HP motor not OK? Many ways are available to ensure that a frequency converter will not exceed a maximum preset speed. The reader's plan was flawed from the beginning, and the problem was not with limiting the maximum speed. Centrifugal pumps follow the affinity laws. When the speed of an electric motor changes due to a change in frequency, other rules dictate the motor's performance.

The HP produced by an induction motor is directly proportional to its torque and rotational speed (HP = (torque x rpm) / 5,250). If the number of stator poles remains constant, the rotational speed of that motor is directly proportional to the frequency of the input power. When the frequency changes so does the speed, but the torque remains constant. For torque to remain constant, HP must change. Therefore, if the incoming power frequency is reduced from 60 Hz to 50 Hz (5/6), the HP will be reduced to 5/6 of its original value. If this is applied to the 10-HP motor in the example above, its output at 50 Hz would be just 8.3 HP. Even though the power required by the pump was reduced to about 57 percent (8.7 HP) of its original 60 Hz value, it is still more than the 10-HP motor can supply at 50 Hz.

U.S.-made motors for 60-Hz operation must be de-rated for use overseas on 50-Hz power. The standard de-rating factor for 230-, 460- and 575-volt models is 5/6 (0.83) of the 60-Hz power. Most manufacturers use 0.85 for open drip proof (ODP) motors and 0.80 for totally enclosed fan-cooled (TEFC) motors, assuming a service factor of 1 and line voltages of 190, 380 and 475 volts. If line voltages are higher, the de-rating factor is reduced proportionally.

Application of the proper line voltage at reduced frequencies is important. A motor designed for 460-volt, 60-Hz operation has a volts/hertz (V/Hz) ratio of 7.66. If the same voltage is used at 50 Hz, the ratio increases to 9.2. To accommodate this increase, the motor magnet's circuit size must increase. Because this is impossible, the existing circuit will saturate, causing an increase in current draw and a corresponding increase in winding temperature. Winding temperature plays a major role in insulation life. For 50-Hz operation, line voltage is reduced to 380 volts and keeps the V/Hz ratio at 7.66.

A constant V/Hz ratio is always maintained when a motor is under frequency converter control. When frequency is changed, the line voltage is automatically compensated via pulse width modulation (PWM). If voltage is 460 volts at 60 Hz, it is reduced to 230 volts at 30 Hz.

Figure 1. Relationship for a 15-horsepower motor and a pump with a full-speed power requirement of 15 horsepower

One reason frequency converter is popular in the centrifugal pump industry is the third affinity law: power varies as the cube of a change in speed. If speed is reduced to 75 percent of full speed, power is reduced to 42 percent of full-speed power. If a pump motor is properly sized for full-speed operation, it will always have adequate power at reduced speeds. Motor power reduction is directly proportional to speed reduction while the pump power requirement drops as the cube of a speed reduction. Figure 1 shows this relationship for a 15-HP motor and a pump with a full-speed power requirement of 15 HP.

Figure 2. Relationship for a 10-horsepower motor and the same pump shown in Figure 1

The ratio of available motor HP to required pump HP increases exponentially as speed is reduced. Figure 2 shows this relationship for the same pump and a 10-HP motor. Here, the available HP does not meet the required HP until the speed is below 50 Hz. If the reader's design point could have been met at 45 Hz, the 10-HP motor would have been adequate.

applicable. very interesting.